There are two ways you can set the time on your NT-RELAY. The first option is to set the time through the Command Center software. Depending on which version of the Command Center you are using the menu will vary slightly. First select the tab at the top of the screen labeled tasks. From the drop down menu you will either select set controller clock or set relay clock. You will get a pop up that will ask if you want to sync the time. Click okay to set the time.
This depends on what you are looking to do and what hardware you have. If you are using the StrongMesh/XBus system and would like to keep everything on a LAN, the Command Center would be your preferred solution. If you want to be able to access the Command Center from multiple places you can set up a VPN to the machine running the Command Center. Alternatively if you do not wish to setup a VPN and still want to be able to access your setup remotely you can sign up for the netx-web service.
Yes, as long as you are using a supported OS.
My thermostat is changing modes without user action on the hardware and scheduling is off in the software. What could be causing this issue?
All schedules must be in chronological order even if the schedules are inactive.